If you’ve been reading our blogs, we’ve looked at load bank testing and how often it should be done. Today we’re examining pre-testing procedures to take into account as you implement load bank testing into your regular operations.
It is important to follow a checklist of best practices during the testing process. This ensures safety for both the test worker while preventing the odds that major power outage will occur during the testing procedure. Though the testing procedure isn’t itself complicated, it does take knowledge to properly perform.
Starting and operating the generator, the technician continues until water temperature stabilization occurs. All manual or automatic switches are then moved to the source of the emergency. The generator will then be loaded step by step with the load bank before reaching the desired load point. The technician removes the load bank load first after the check and transfers all switches back to the normal position before allowing the generator to cool down per the instructions of the manufacturer.
This update is by A&A Power Generators, a national company providing Dedicated Power Systems with global reach. Our mission is to meet emergency power needs by delivering dedicated power solutions and services for residential and commercial markets in ways that are economically and environmentally sustainable. We aim to be your sole choice for new Generac generator, Kohler power generators, natural gas, and diesel-fueled solutions as well as service and maintenance repair, with decades of power industry experience. For more information on mobile heaters or other questions, please call 1-888-991-4500.